Open intelACe Top Cover; insert screw driver in notch and twist clockwise. Top Cover is easily removed exposing the intelACe Bottom Assembly. Take care not to touch the Main Controller PCBA which will be mounted on Bottom Cover
Technology & Installation
intelACe provides a smart control which is an improvement upon existing thermostat based control in Air Cons. Optimization of compressor operation under all user and environment conditions are achieved.
- Compressor control is an active and intelligent.
- Prevention of thermodynamic saturation.
- Full utilization of cooling capacity in cooling coil (heat exchanger).
intelACe accurately measures the room temperature and detects the compressor duty cycle. This information is processed by intelACe which then implements intelligent control over the compressor.
This approach ensures the required room temperature is achieved, optimal compressor operation achieved and thermodynamic saturation of refrigerant (energy wastage) is avoided.
The intelligent control ensures room temperature is maintained within 0.5°C of the setpoint and is displayed. Temperature max and min readings are able recorded and displayed at the press of a button.
intelACe can be installed to all existing Air Conditioners of any size and Commercial Refrigerant units:
- Non-Inverter and Inverter
- Wall Mount & Cassette
- Single Phase & 3 Phase
Mark Drill Hole Location; position intelACe Bottom Assembly near the Air Conditioner (suitable location within 3mm) and mark the mounting hole location.
Drill Mounting Holes; drill 2 holes to a depth of 25mm (1”) at the marked location using 4mm masonry drill bit..
Mount intelACe On Wall; place intelACe Bottom Assembly on wall, aligning the mounting hole to wall plugs. Once aligned, insert the provided mounting screws into the wall plug and screw it using a Phillips screw driver.
Attach intelACe Top Cover; properly intelACe Top Cover on the wall mounted intelACe Bottom Assembly and push it to snap in place. Inspect the attachment to ensure intelACe Top Cover is properly attached with all the locking ribs attached.
intelACe is easily and safely installed in less than 10minutes, without any modifications.
Any electrician or Air Con technician can install intelACe following the installation manual with ZERO setup.
Typically, there are 4 cables coming out from intelACe main unit.
- Power supply cable (L) – Brown colour
- Power supply cable (N) – Blue colour
- Compressor Control Cable 1 – Black Colour
- Compressor Control Cable 2 – Black Colour
CAUTION! INSTALLATION TO BE DONE BY EXPERIENCED & QUALIFIED ELECTRICIAN OR TECHNICIAN. ENSURE THE POWER SUPPLY TO THE AIR CONDITIONER IS COMPLETELY SHUT BEFORE PROCEEDING. USE A VOLTAGE DETECTOR TO CONFIRM ABSENCE OF VOLTAGE AND INSTALL A LOCK-OUT TO PREVENT ACCIDENTAL ENERGIZATION.